This article is supplementary to the ultimate guide to balancing, please also check that out!
Many modern condensing boilers will do this to a certain degree but perhaps not optimally. There is a very practical and simple tool to accurately measure flow rates in heating systems that don't involve installing flow gauges or any unnecessary fittings. Delta T.
Delta T (or DT) simply refers to the temperature difference. If we measure the temperature difference on either side of an emitter or heat source, we can work out the flow rate in litres per second through it, providing we know the heat input or output of that component. For the purpose of this article, I'm not going to go into the maths, but there will be an article on mass flow rate available soon. Or watch our mass flow rate Youtube Video and article coming soon.
To keep it simple, a faster flow rate will give a smaller DT across your heat source or emitter and a slower flow rate gives a wider DT. If you have the correct speed at your pump you will have the correct DT at the heat source and importantly, visa versa.
Because the flow rate and DT are completely linked in this way we can simply target a DT at our emitters and heat source rather than working out any specific flow rates. Generally speaking with heat pumps we would aim for a DT of 5-7°c and for gas boilers a DT of 20°c, turn up the pump if the DT is too wide and down if too narrow.
Many modulating boilers automatically adjust the pump speed to target dT20, these can be quickly checked, and many have settings for refinement. All heat-only boilers will of course need the pump to be set manually.
You may have some individual radiators on the system that have too much temperature difference and some with too little, but if your overall flow rate is correct you will still have the correct DT at the heat source as the return temperatures will equalize when they tee in together. This is why balancing radiators only have a minimal effect on increasing condensing.
Finally then, how do we put this into practice?
Also bear in mind this does not need to be 100% accurate!!. Read more at Do we really need DT20?
Enjoyed this article? Want to know more about system design and how to become a top heating engineer?